In designing a pump station many times you need to balance efficiency and performance. An ultra conservative approach often leads to large pump stations that may an opposite affect on performance where larger volumes result in lower sump velocities, settling of solids, and stagnant conditions that can lead to damaging surface vortices and odors. Poorly designed stations can also lead to high operation and maintenance costs, clogging of impellers and damage to pumps.
Watch Flygt’s video on how to optimize your pump station design.
Flygt’s experience and research helps customers design pump stations that minimize costs related to investment, footprint, and energy consumption and maximize the station and pumps performance. One of the things that Flygt’s research has shown, for example, is that smaller pump stations can improve hydraulic performance and help avoid problems with stagnant areas.
利用des Flygt预制站igns that are based on the results from computational fluid dynamics (CFD), physical modeling and verification with real-world installations. Flygt’s “SECAD” pump station tool provides in minutes, a customized design based on an approved Hydraulic Institute (HI) Standards large station design. A complete 3D design is provided with AutoCAD drawings with self-cleaning design and uniform approach flow to the pumps with no adverse hydraulic phenomena, eliminate issues with sediment or floating debris, eliminate or reduce the costs relate to cleaning and maintenance. Ultimately, these improvements benefit our customers through lower cost and reduced risk related to pump station construction and operation.
Whatever your pump station challenges, we can help you easily find the solution that works best for you. Whether it is designing an entirely new pump station, or improving an existing one. Our broad range of products will also help you ensure trouble-free operation.
Featuring Qty 4 Flygt Model 3800, 42″, 300 HP Submersible Pumps and 42″ Low Head Ball Check Valves
In order to remediate the excess inlet pre-swirl and submerged vortices observed in the analyses performed on the original design, several changes to the sump geometry have been recommended and subsequently tested. These changes are illustrated in Figures 19 and 20 below. Figure 19 is a CAD rendering of the station showing a repositioned inflow pipe to a lower elevation and an increase in both high and low water levels. Changing inflow pipe elevation and water levels means there will be more energy dissipated in the inflow region before the flow enters the sump.
Bulk flow patterns from Case 1d, the low water case with Pump 4 in service, are shown below in Figure 21. The upper illustration shows the case before and the lower illustration shows the case after modification. One can note that the increased depth results in much lower velocities in the inlet channels. There is still some skewness of the flow in these channels, but it is not as severe as was the case with the original geometry.
The Bulk Flow Patterns shown in Figure 22 are from the high water Case 2d.Like the low water cases, the skewness of the incoming flow is significantly reduced in the modified sump. The water level in the modified case is sufficiently high so that there is some flow passing over the wall separating the inflow area from the sump. This also helps lower the velocities in the inflow channels.
Eliminate Submerged Vortices
Figure 20 shows some geometry changes proposed to diminish the likelihood of submerged vortices that might enter the pump intakes. In some of the pumps in the high water cases, potential vortices were observed directly beneath the pump intakes. Circulation zones that can develop in this location are common due to there being flows from several directions that come together here. Filling in these regions with a solid is a remedial approach that is effective. To that end, the benching on the splitter beneath the pump is extended to 6 ft 5 in from the plinth wall. Vortices that form on the plinth wall are typical in centrifugal pump installations of this type because there is often flow moving downward around either side of the pump discharge connection and initiating a re-circulating flow pattern. Fins attached to the upper part of the plinth wall will break up any re-circulating flow patterns that form there.
Sites for potential surface vortices in the high water case are identified in Figure 7 below. This is a plot of streaklines originating on the water surface. Re-circulation zones are a tell tale sign of potential vortexing.
The CFD models run in this study indicate that the Pump Station will operate in a satisfactory manner for pumping conditions within the range of cases tested. These recommended changes comprise elevated water levels for both high and low water operational points, lower elevation for the station inflow pipe, extended benching on the splitter beneath the pump intakes and installing fins on the plinth walls.
该项目的CFD分析很重要识别泵方法流动问题。在使用一个泵的低水箱中，通过四个流入通道进入贮槽的流量偏离从流入管最远的每个通道的一侧。这种偏斜是通过入口管进入站的流量高速度的结果，并产生观察到的高泵的预旋转角度。该站的流入部分从贮槽中分离，其中泵由壁壁，从而形成横向流入通道。进入贮槽的所有水通过该流入通道的地板上的孔并通过四个往泵的通道。此时，水具有显着的横向组分，这导致泵方法中观察到的偏斜。增加流入通道中的水量将允许该区域中的一些能量在进入贮槽之前散发。具有三个泵中的高水箱呈现出偏斜的方法，类似于低水箱中观察到的流量模式，但由于流入通道中的水量增加，这些速度不太严重。高水位案例的水位增加应该有助于进一步帮助。在高水位和低水位壳体中观察到的涡流是典型的潜水式离心泵装置。 Modifying the benching beneath the pumps and roughening up the plinth walls behind the pumps are typical fixes for these flow problems. Changes to the pump station design to remediate the adverse flow conditions were tested. These included elevated water levels for both high and low water operational points, lower elevation for the station inflow pipe, extended benching on the splitter beneath the pump intakes and fins on the plinth walls. Lowering the inlet pipe elevation and elevating the water levels brought about a significant improvement regarding the skewness observed in the approach flows. As a result, pump inlet pre-swirl angles diminished to within the acceptable range. The benching and fin additions used to eliminate submerged vortices were effective as well.